Chilled Water Systems
The District Cooling System for the main campus consists of five chiller plants with a combined capacity of 50,000 tons. The plants are interconnected by underground piping and operated as one production system using a networked Supervisory Control and Data Acquisition (SCADA) system. From a single console, operators can manage and balance loads among the chiller plants, use capacity anywhere in the system and continue operating in critical areas despite cooling equipment failure or utility outages.
Two of the chiller plants house both steam absorption and electric centrifugal chillers; the other three house only electric centrifugal chillers, allowing us to quickly respond to outages of either energy source, as well as manage costs by monitoring the local electric utility’s hourly pricing program.
The Operations Center also includes a five million gallon stratified cold water storage tank. The thermal storage system shifts a portion of the University’s chilled water production to off-peak periods, reducing the need for electric purchases from Duke Energy during peak times.
After it is chilled, the water flows into a loop piping system, which distributes the water to bridge interface systems that control the flow of chilled water in and out of each of the campus buildings. These bridge interface systems ensure that the buildings receive and efficiently use the chilled water to meet their cooling demand. When the water has been used (warmed), it is returned to a chiller plant to be chilled again.
In addition, Chilled Water Systems manages eight stand-alone chillers.
System Design and Capacity
The University owns, maintains and operates a district cooling system comprised of five production plants, a thermal energy storage system, a distribution system with over 22 miles of underground piping and building bridge systems consisting of over 150 bridges servicing over 140 locations. See How Things Work for an illustration of how the District Cooling System interrelates with our other campus energy systems.
Production PlantDate BuiltElectrical Centrifugal ChillersSteam Absorption ChillersTons Capacity
|North Chiller Plant||1970||8||3||12,750|
|Cobb Chiller Plant||2006||5||—||10,000|
|South Chiller Plant||1976||10||2||19,000|
|East Chiller Plant||1983||3||—||2,635|
The University also operates and maintains remote electrical centrifugal chiller systems which generally serve individual building(s) that cannot be serviced by the distribution system.
Remote SystemTons Capacity
|Aycock Family Medicine||187|
|Child Development Center||80|
|440 West Franklin||253|
Energy Services Maps
- All Utilities
- Chilled Water
- Whiteway (Lights)
- Wastewater & Reclaimed Water
- Energy Dashboard
- Customer Billing Portal
- Policies and Procedures
- Employee Portal
- Three Zeros Environmental Initiative
925 Branch St.
Chapel Hill, NC 27599